User manual ELECTROLUX WP71-265WT
DON'T FORGET : ALWAYS READ THE USER GUIDE BEFORE BUYING !!!
If this document matches the user guide, instructions manual or user manual, feature sets, schematics you are looking for, download it now. Diplodocs provides you a fast and easy access to the user manual ELECTROLUX WP71-265WT. We hope that this ELECTROLUX WP71-265WT user guide will be useful to you.
Manual abstract: user guide ELECTROLUX WP71-265WT
Detailed instructions for use are in the User's Guide.
[. . . ] You’ve chosen a product that brings with it decades of professional experience and innovation. So whenever you use it, you can be safe in the knowledge that you’ll get great results every time. Visit our website to: Get usage advice, brochures, trouble shooter, service information: www. Com Buy Accessories, Consumables and Original spare parts for your appliance: www. [. . . ] All maintenance staff and others working in the local area shall be instructed on the nature of work being carried out. Ensure that the conditions within the area have been made safe by control of flammable material. The area shall be checked with an appropriate refrigerant detector prior to and during work, to ensure the technician is aware of potentially flammable atmospheres. Ensure that the leak detection equipment being used is suitable for use with flammable refrigerants, i. If any hot work is to be conducted on the refrigeration equipment or any associated parts, appropriate fire extinguishing equipment shall be available to hand. Have a dry powder or CO2 fire extinguisher adjacent to the charging area. No person carrying out work in relation to a refrigeration system which involves exposing any pipe work that contains or has contained flammable refrigerant shall use any sources of ignition in such a manner that it may lead to the risk of fire or explosion. All possible ignition sources, including cigarette smoking, should be kept sufficiently far away from the site of installation, repairing, removing and disposal, during which flammable refrigerant can possibly be released to the surrounding space. Prior to work taking place, the area around the equipment is to be surveyed to make sure that there are no flammable hazards or ignition risks. Ensure that the area is in the open or that it is adequately ventilated before breaking into the system or conducting any hot work. A degree of ventilation shall continue during the period that the work is carried out. The ventilation should safely disperse any released refrigerant and preferably expel it externally into the atmosphere. Where electrical components are being changed, they shall be fit for the purpose and to the correct specification. At all times the manufacturer’s maintenance and service guidelines shall be followed. If in doubt consult the manufacturer’s technical department for assistance. The following checks shall be applied to installations using flammable refrigerants: – The charge size is in accordance with the room size within which the refrigerant containing parts are installed; – The ventilation machinery and outlets are operating adequately and are not obstructed;
– If an indirect refrigerating circuit is being used, the secondary circuit shall be checked for the presence of refrigerant; – Marking to the equipment continues to be visible and legible. Markings and signs that are illegible shall be corrected; – Refrigeration pipe or components are installed in a position where theyare unlikely to be exposed to any substance which may corrode refrigerant containing components, unless the components are constructed of materials which are inherently resistant to being corroded or are suitably protected against being so corroded. Repair and maintenance to electrical components shall include initial safety checks and component inspection procedures. If a fault exists that could compromise safety, then no electrical supply shall be connected to the circuit until it is satisfactorily dealt with. If the fault cannot be corrected immediately but it is necessary to continue operation, an adequate temporary solution shall be used. This shall be reported to the owner of the equipment so all parties are advised. Initial safety checks shall include: • That capacitors are discharged: this shall be done in a safe manner to avoid possibility of sparking; • That there no live electrical components and wiring are exposed while charging, recovering or purging the system; • That there is continuity of earth bonding. [. . . ] Før arbeid blir utført, må omgivelsene bli undersøkt for å sikre at det ikke finnes fare for brann eller antenning. Hvis det er absolutt nødvendig å ha elektrisk strøm til utstyr under service, så må du ha en permanent form for lekkasjedeteksjon i bruk plassert på det mest kritiske punktet for å advare om en potensielt farlig situasjon. Kabling Kontroller at kabling ikke vil være utsatt for slitasje, korrosjon, for høyt trykk, vibrasjoner, skarpe kanter eller andre uønskede påvirkninger. Metoder for lekkasjepåvisning Følgende metoder for å oppdage lekkasjer er godkjent for systemer som inneholder brennbare kjølemidler. [. . . ]
DISCLAIMER TO DOWNLOAD THE USER GUIDE ELECTROLUX WP71-265WT
Click on "Download the user Manual" at the end of this Contract if you accept its terms, the downloading of the manual ELECTROLUX WP71-265WT will begin.